24-5. NEUTRAL START SWITCH REPLACEMENT (CONT).
Ensure that transfer case is in
Insert one multimeter test lead in each
socket of neutral start switch connector (1).
Set multimeter select switch to ohms:
If there is no continuity, go to
If there is continuity, go to Step (3).
Loosen neutral start switch (2) until circuit
tester indicates no continuity. Then, loosen
switch 3/4 turn more.
It may be necessary to turn gear
to shift transfer case into low
gear in Step (4).
Shift into low gear by pushing rod end (3)
toward housing (4).
If multimeter indicates continuity, go
to Step (6).
If multimeter indicates no continuity,
check multimeter connections. If
multimeter still shows no continuity,
continue with Step (5).
Tighten neutral start switch (2) and
adapter (5) until multimeter indicates
continuity. Then, tighten another 3/4 turn.